Botou Youjian Environmental Protection Equipment Co. LTD.[Hebei,China] Business Type: ManufacturerMain Mark: Africa , Americas , Asia , Caribbean , East Europe , Europe , Middle East , North Europe , Oceania , Other Markets , West Europe , WorldwideExporter: 11% - 20%Certs: FAMI-QS, GB, ISO9001, ISO9002Description: Boiler Pulse Deduster,Boiler Bag Dust Collector,Pulse Bag Filter
Place of Origin: Botou city, hebei province, China
The working principle of the pulsate bag Dust Collector of the boiler: The boiler pulse Bag Filter is composed of ash hopper, upper box, middle box, cloth bag, ash cleaning and blowing device. When working, the high temperature flue gas flows into the ash bucket from the inlet of the ash bucket. Due to the gravity settlement, the coarse dust particles directly fall into the bottom of the ash bucket and play the role of precollecting dust. At the same time, the velocity of the air flow becomes slow, and the slight dust enters the middle box with the turning of the air flow, and the dust is filtered and hindraged by the high temperature filter bag, and the dust is attached to the outer surface of the filter bag and filtered after the filter. The gas passes through the filter bag into the upper box to the air outlet, and is discharged to the atmosphere by the induced draft fan. The dust accumulated on the outer wall of the filter bag is constantly increasing. When the setting time is reached, the pulse controller is triggered by the sequential interval of the pulse controller to open the Pulse Solenoid Valve, so that the compressed air in the compressed air bag is pulsated by the blowpipe to the filter bag and pulsates the ash, so that the filter bag will suddenly shake off the dust attached to the outer wall of the filter bag, and peel the filter bag from the filter bag. The dust discharged to ash hopper is discharged through the ash discharge gate valve. Performance characteristics of boiler pulse bag dust collector: 1, the boiler pulse bag dust collector adopts the lower intake air, which plays the role of dust collecting, avoiding the dust gas directly scouring the bag, reducing the dust concentration of the dust gas, and prolonging the life of the filter bag and the pulse solenoid valve. 2. The sealing materials used in the boiler pulse bag filter are all made of high temperature resistant materials. 3. The ash blowing and blowing pipe is lengthened so that the pulse electromagnetic valve is far away from the high temperature flue gas and the damage of the valve plate of the pulse solenoid valve is avoided. 4. The filter bag of the pulse bag filter of the boiler adopts the high temperature filter bag to treat the flue gas temperature <250 degrees Celsius. 5, the bag bag mouth adopts elastic expansion ring, good sealing performance, solid and reliable. 6. The filter bag skeleton is circular, which reduces the friction between the filter bag and the skeleton, prolongs the life of the filter bag, and is convenient for unloading the bag. 7. The upper bag can be replaced by opening the top cover door while changing the bag. After the skeleton is drawn, the bag can be changed and the operation condition of the bag changing is improved. 8. Dust control is controlled by time, and the filter bags are cleaned in turn according to the set time and every cleaning cycle. Looking for ideal Boiler Pulse Deduster Manufacturer & supplier ? We have a wide selection at great prices to help you get creative. All the Boiler Bag Dust Collector are quality guaranteed. We are China Origin Factory of Pulse Bag Filter. If you have any question, please feel free to contact us.